National Instruments FP-PS-4 manual
- Read online or download the manual
- 11 pages
- 0.5 mb
Go to page of
Similar user manuals
National Instruments PXI-10457 pages 0.19 mb
National Instruments FP-PS-411 pages 0.5 mb
National Instruments PXI-10426 pages 0.15 mb
National Instruments NI PXI-10065 pages 0.12 mb
National Instruments NI PXI-1042 Series8 pages 0.23 mb
A good user manual
The rules should oblige the seller to give the purchaser an operating instrucion of National Instruments FP-PS-4, along with an item. The lack of an instruction or false information given to customer shall constitute grounds to apply for a complaint because of nonconformity of goods with the contract. In accordance with the law, a customer can receive an instruction in non-paper form; lately graphic and electronic forms of the manuals, as well as instructional videos have been majorly used. A necessary precondition for this is the unmistakable, legible character of an instruction.
What is an instruction?
The term originates from the Latin word „instructio”, which means organizing. Therefore, in an instruction of National Instruments FP-PS-4 one could find a process description. An instruction's purpose is to teach, to ease the start-up and an item's use or performance of certain activities. An instruction is a compilation of information about an item/a service, it is a clue.
Unfortunately, only a few customers devote their time to read an instruction of National Instruments FP-PS-4. A good user manual introduces us to a number of additional functionalities of the purchased item, and also helps us to avoid the formation of most of the defects.
What should a perfect user manual contain?
First and foremost, an user manual of National Instruments FP-PS-4 should contain:
- informations concerning technical data of National Instruments FP-PS-4
- name of the manufacturer and a year of construction of the National Instruments FP-PS-4 item
- rules of operation, control and maintenance of the National Instruments FP-PS-4 item
- safety signs and mark certificates which confirm compatibility with appropriate standards
Why don't we read the manuals?
Usually it results from the lack of time and certainty about functionalities of purchased items. Unfortunately, networking and start-up of National Instruments FP-PS-4 alone are not enough. An instruction contains a number of clues concerning respective functionalities, safety rules, maintenance methods (what means should be used), eventual defects of National Instruments FP-PS-4, and methods of problem resolution. Eventually, when one still can't find the answer to his problems, he will be directed to the National Instruments service. Lately animated manuals and instructional videos are quite popular among customers. These kinds of user manuals are effective; they assure that a customer will familiarize himself with the whole material, and won't skip complicated, technical information of National Instruments FP-PS-4.
Why one should read the manuals?
It is mostly in the manuals where we will find the details concerning construction and possibility of the National Instruments FP-PS-4 item, and its use of respective accessory, as well as information concerning all the functions and facilities.
After a successful purchase of an item one should find a moment and get to know with every part of an instruction. Currently the manuals are carefully prearranged and translated, so they could be fully understood by its users. The manuals will serve as an informational aid.
Table of contents for the manual
FieldPoint™, National Inst ruments™, NI™, and ni.com™ are trademarks of National Instruments Corporation. Product and company names ment ioned herein are trade marks or trade names of thei r respective companies. 323179A-01 © 2001 National Ins truments Corp. All rights reserv ed. November 2001 OPERA TING INSTRUCTIONS FP-PS-4 FieldPoint Pow[...]
FP-PS-4 Operating Instructions 2 ni.com 1. Use a flat-bladed screwdr iv e r to unlock the DIN rail clip, as s h o w ni nF i g u r e1 . Figure 1. Unlocking the Rail Clip 2. Attach the lip on the rear of the FP-PS-4 onto t he top of a 35 mm DIN rail and press it do wn onto the DIN rail, as sho wn in Figure 2. Figure 2. Attaching the Module to a DIN R[...]
© National Instruments Corp. 3 FP-PS-4 Operating Instructions 3. Slide the FP-PS-4 to the desired position along the DIN rai l. For max imum cooling, lea v e a 25 mm (1.0 in.) space between the FP-PS-4 and other devices on your DIN rail. After it is in position, lock it to the DIN rail b y pushing the rail clip to the locked position, as sho wn in[...]
FP-PS-4 Operating Instructions 4 ni.com Mounting Y our FP-PS-4 on a Panel Follo w these steps to install the optional FieldPoint network panel mount accessory and mount the FP-PS-4 po wer supply module to a panel. Y ou can order the panel mount accessory , part number 777609-01, from National Instruments. 1. Use a flat-bladed scre wdri ver to unloc[...]
© National Instruments Corp. 5 FP-PS-4 Operating Instructions 4. Mount the FP-PS-4 to your panel with the panel mount accessory , as sho wn in Figure 5. The installation guide that comes with the panel mount accessory includes a template that you can use to drill pilot holes for mounting FieldPoint modules. For maximum cooling, lea ve a 25 mm (1.0[...]
FP-PS-4 Operating Instructions 6 ni.com needs. Select one or a combination of the methods to po wer the signals of each of yo ur I/O modules: • The signals of the I/O module are po wered by an FP- PS-4 that is connected to only that I/O module. • The signals of the I/O module share an FP-PS-4 with a neighboring I/O module or network module. Thi[...]
© National Instruments Corp. 7 FP-PS-4 Operating Instructions Ensure that all the wiring is installed according to local codes and regulations b y qualif ied electrical personnel. Follo w these steps to connect the FP-PS-4 to your FieldPoint system. 1. Use a 16 to 26 A WG stranded wire to connect the FP-PS-4 to your FieldPoint network module or I/[...]
FP-PS-4 Operating Instructions 8 ni.com 6. Connect the green or green/yellow conductor into the ground terminal. Caution When you install the conductors, make sure that the entire conductor is in the screw terminal and that there are no loose strands outside of the termi nal. Only install one wire in each terminal. Specifications The following spec[...]
© National Instruments Corp. 9 FP-PS-4 Operating Instructions Overload protection ....... ........... ........ Protected against short circuits and output ov erload Physical Indicator .......... ........ ......... ............ ..... Green DC PO W ER LED W eight .... ........... ......... ........... ......... ... 300 g (10.5 oz) Environmental Fiel[...]
FP-PS-4 Operating Instructions 10 ni.com regulatory compliance information. T o obtain the DoC for this product, cli ck Declaration of Conformity at ni.com/hardref.nsf/ . Mechanical Dimensions Figure 9 sho ws the mechanical dimensions of the FP-PS-4. Dimensions are giv en in millimeters [inch es]. Figure 9. Mechanical Dimensions 109.5 [4.31] 91.44 [...]
© National Instruments Corp. 11 FP-PS-4 Operating Instructions Where to Go for Support For more informatio n about setting up your FieldPoint system, refer to these National Instruments documents: • Y our FieldPoint network module user manual • Y our other FieldPoint I/O module operating instructions • Y our FieldPoint terminal base operatin[...]