National Instruments EIGHT CHANNEL SPST RELAY MODULE manual
- Read online or download the manual
- 14 pages
- 0.35 mb
Go to page of
Similar user manuals
National Instruments CFP-RLY-42114 pages 0.35 mb
National Instruments NI-845x Software and Hardware6 pages 0.09 mb
National Instruments EIGHT CHANNEL SPST RELAY MODULE14 pages 0.35 mb
National Instruments NI-845x6 pages 0.09 mb
A good user manual
The rules should oblige the seller to give the purchaser an operating instrucion of National Instruments EIGHT CHANNEL SPST RELAY MODULE, along with an item. The lack of an instruction or false information given to customer shall constitute grounds to apply for a complaint because of nonconformity of goods with the contract. In accordance with the law, a customer can receive an instruction in non-paper form; lately graphic and electronic forms of the manuals, as well as instructional videos have been majorly used. A necessary precondition for this is the unmistakable, legible character of an instruction.
What is an instruction?
The term originates from the Latin word „instructio”, which means organizing. Therefore, in an instruction of National Instruments EIGHT CHANNEL SPST RELAY MODULE one could find a process description. An instruction's purpose is to teach, to ease the start-up and an item's use or performance of certain activities. An instruction is a compilation of information about an item/a service, it is a clue.
Unfortunately, only a few customers devote their time to read an instruction of National Instruments EIGHT CHANNEL SPST RELAY MODULE. A good user manual introduces us to a number of additional functionalities of the purchased item, and also helps us to avoid the formation of most of the defects.
What should a perfect user manual contain?
First and foremost, an user manual of National Instruments EIGHT CHANNEL SPST RELAY MODULE should contain:
- informations concerning technical data of National Instruments EIGHT CHANNEL SPST RELAY MODULE
- name of the manufacturer and a year of construction of the National Instruments EIGHT CHANNEL SPST RELAY MODULE item
- rules of operation, control and maintenance of the National Instruments EIGHT CHANNEL SPST RELAY MODULE item
- safety signs and mark certificates which confirm compatibility with appropriate standards
Why don't we read the manuals?
Usually it results from the lack of time and certainty about functionalities of purchased items. Unfortunately, networking and start-up of National Instruments EIGHT CHANNEL SPST RELAY MODULE alone are not enough. An instruction contains a number of clues concerning respective functionalities, safety rules, maintenance methods (what means should be used), eventual defects of National Instruments EIGHT CHANNEL SPST RELAY MODULE, and methods of problem resolution. Eventually, when one still can't find the answer to his problems, he will be directed to the National Instruments service. Lately animated manuals and instructional videos are quite popular among customers. These kinds of user manuals are effective; they assure that a customer will familiarize himself with the whole material, and won't skip complicated, technical information of National Instruments EIGHT CHANNEL SPST RELAY MODULE.
Why one should read the manuals?
It is mostly in the manuals where we will find the details concerning construction and possibility of the National Instruments EIGHT CHANNEL SPST RELAY MODULE item, and its use of respective accessory, as well as information concerning all the functions and facilities.
After a successful purchase of an item one should find a moment and get to know with every part of an instruction. Currently the manuals are carefully prearranged and translated, so they could be fully understood by its users. The manuals will serve as an informational aid.
Table of contents for the manual
323617A-01 May 2003 © 2003 National I nstruments Corp. Al l rights res erved. FieldPoint™, Nati o[...]
cFP-RLY-421 2 ni.com Before you conf igure a FieldPoint system that uses a cFP-RL Y -421 module, cal[...]
© National Instruments Corp. 3 cFP-RLY-421 Figure 1. Installing the cFP-RL Y -421 Wiring the cFP-RL[...]
cFP-RLY-421 4 ni.com T able 1 li sts the terminal assign ments for the signals of each channel. All [...]
© National Instruments Corp. 5 cFP-RLY-421 Connecting Loads to the cFP-RL Y -421 W ire an external [...]
cFP-RLY-421 6 ni.com In addition, the cFP-RL Y -421 has internal protection MO Vs to pre vent excess[...]
© National Instruments Corp. 7 cFP-RLY-421 Diode Circuit CR Circuits Varistor Circuit Diagram Notes[...]
cFP-RLY-421 8 ni.com In-Rush Current The type of l oad and its in-rush current charac teristics, tog[...]
© National Instruments Corp. 9 cFP-RLY-421 Upgrading the FieldPoint Firmware Y ou may need to upgra[...]
cFP-RLY-421 10 ni.com •D o not share the exter nal supply voltages (the V and C terminals) with ot[...]
© National Instruments Corp. 11 cFP-RLY-421 Specifications The follo wing specifications ar e typic[...]
cFP-RLY-421 12 ni.com Physical Indicators ..... .............. ........... ........... . Green POWER[...]
© National Instruments Corp. 13 cFP-RLY-421 Safety This product is designed to meet the requirement[...]
cFP-RLY-421 14 ni.com Where to Go for Support For more information about settin g up the FieldPoint [...]