National Instruments RS-485 manual
- Read online or download the manual
- 8 pages
- 0.26 mb
Go to page of
Similar user manuals
National Instruments PXI-846x Series60 pages 0.81 mb
National Instruments MID-765436 pages 0.75 mb
National Instruments 734466 pages 0.5 mb
National Instruments TPC-201247 pages 0.64 mb
National Instruments NI 922934 pages 0.41 mb
National Instruments SCC-TC0220 pages 0.22 mb
National Instruments SCC-AI0218 pages 0.2 mb
National Instruments SCC-AI0118 pages 0.2 mb
A good user manual
The rules should oblige the seller to give the purchaser an operating instrucion of National Instruments RS-485, along with an item. The lack of an instruction or false information given to customer shall constitute grounds to apply for a complaint because of nonconformity of goods with the contract. In accordance with the law, a customer can receive an instruction in non-paper form; lately graphic and electronic forms of the manuals, as well as instructional videos have been majorly used. A necessary precondition for this is the unmistakable, legible character of an instruction.
What is an instruction?
The term originates from the Latin word „instructio”, which means organizing. Therefore, in an instruction of National Instruments RS-485 one could find a process description. An instruction's purpose is to teach, to ease the start-up and an item's use or performance of certain activities. An instruction is a compilation of information about an item/a service, it is a clue.
Unfortunately, only a few customers devote their time to read an instruction of National Instruments RS-485. A good user manual introduces us to a number of additional functionalities of the purchased item, and also helps us to avoid the formation of most of the defects.
What should a perfect user manual contain?
First and foremost, an user manual of National Instruments RS-485 should contain:
- informations concerning technical data of National Instruments RS-485
- name of the manufacturer and a year of construction of the National Instruments RS-485 item
- rules of operation, control and maintenance of the National Instruments RS-485 item
- safety signs and mark certificates which confirm compatibility with appropriate standards
Why don't we read the manuals?
Usually it results from the lack of time and certainty about functionalities of purchased items. Unfortunately, networking and start-up of National Instruments RS-485 alone are not enough. An instruction contains a number of clues concerning respective functionalities, safety rules, maintenance methods (what means should be used), eventual defects of National Instruments RS-485, and methods of problem resolution. Eventually, when one still can't find the answer to his problems, he will be directed to the National Instruments service. Lately animated manuals and instructional videos are quite popular among customers. These kinds of user manuals are effective; they assure that a customer will familiarize himself with the whole material, and won't skip complicated, technical information of National Instruments RS-485.
Why one should read the manuals?
It is mostly in the manuals where we will find the details concerning construction and possibility of the National Instruments RS-485 item, and its use of respective accessory, as well as information concerning all the functions and facilities.
After a successful purchase of an item one should find a moment and get to know with every part of an instruction. Currently the manuals are carefully prearranged and translated, so they could be fully understood by its users. The manuals will serve as an informational aid.
Table of contents for the manual
FieldPoint ™ is a trademark of National Instruments Corporation. Product and company names are trademarks or trade names of their respective companies. 321698A-01 © Copyright 1997 National Instruments Corp. All rights reserved. July 1997 FP-1001 FieldPoint RS-485 Network Module Highlights • Isolated RS-485 interface to host computer or to FP-1[...]
2 The FP-1001 has a simple rail clip for mounting reliably onto a standard 35 mm DIN rail. To install the FP-1001 to the DIN rail, follow these steps: 1. With a flat bladed screwdriver, open the DIN rail clip to the unlocked position as shown in Figure 1. Figure 1. DIN Rail Clip 2. Hook the lip on the rear of the FP-1001 onto the top of a 35 mm DIN[...]
3 Figure 3. Installed Network Module Network Connection Connect the FP-1001 to a host computer, or to the RS-485 repeater port of an FP-1000, using the 5 position Combicon screw terminal adapter of the RS-485 connector on the FP-1001. You may connect up to 25 FP-1001 network modules to a single RS-485 port of a host computer, or up to 24 FP-1001 ne[...]
4 The RX+ of the host port (or FP-1000 RS-485 repeater port) must be connected to the TX+ of all of the FP-1001 modules, and the RX- of the host port (or FP-1000 RS-485 repeater port) must be connected to the TX- of all of the FP-1001 modules. This pair of connections provides communication to the host computer from the FP-1001 modules. These conne[...]
5 modules on different serial ports may have the same address. Every module on one serial port of a host computer must have the same baud rate. Figure 6. Address and Baud Rate Switch Switches 1-5 set the network address of the FP-1001. The addresses of the terminal bases connected to the network module are automatically configured to be sequentiall[...]
6 Switches 6-8 set the baud rate of the FP-1001. Table 2 shows the switch positions and the corresponding network baud rates. 40 170 50 180 60 190 70 200 80 210 90 220 100 230 110 240 120 Other Settings Not Allowed Table 2. Baud Rate Switch Settings Switch Positions 6-8 Network Module Baud Rate Switch Positions 6-8 Network Module Baud Rate 300 1920[...]
7 Powering the FP-1001 NOTE: Terminal bases must be connected to the FP-1001, and the baud rate switch must be set, before power is applied to the FP-1001. An 11-30 VDC power supply is required by each FieldPoint stack. The network module filters and regulates this supplied power and provides power for all the I/O modules in the stack. Therefore yo[...]
RS-485 isolation ............................... 2500 Vrms breakdown, 250 Vrms operational Power Consumption.......................... 1 W + 1.15 * ∑ (I/O module power requirements ) Operating Temperature ..................... -40 °C to +70 °C Storage Temperature ......................... -55 °C to + 100 °C Relative Humidity .................[...]