Friedrich CP14-18-24 CP14N10 manual
- Read online or download the manual
- 28 pages
- 1 mb
Go to page of
A good user manual
The rules should oblige the seller to give the purchaser an operating instrucion of Friedrich CP14-18-24 CP14N10, along with an item. The lack of an instruction or false information given to customer shall constitute grounds to apply for a complaint because of nonconformity of goods with the contract. In accordance with the law, a customer can receive an instruction in non-paper form; lately graphic and electronic forms of the manuals, as well as instructional videos have been majorly used. A necessary precondition for this is the unmistakable, legible character of an instruction.
What is an instruction?
The term originates from the Latin word „instructio”, which means organizing. Therefore, in an instruction of Friedrich CP14-18-24 CP14N10 one could find a process description. An instruction's purpose is to teach, to ease the start-up and an item's use or performance of certain activities. An instruction is a compilation of information about an item/a service, it is a clue.
Unfortunately, only a few customers devote their time to read an instruction of Friedrich CP14-18-24 CP14N10. A good user manual introduces us to a number of additional functionalities of the purchased item, and also helps us to avoid the formation of most of the defects.
What should a perfect user manual contain?
First and foremost, an user manual of Friedrich CP14-18-24 CP14N10 should contain:
- informations concerning technical data of Friedrich CP14-18-24 CP14N10
- name of the manufacturer and a year of construction of the Friedrich CP14-18-24 CP14N10 item
- rules of operation, control and maintenance of the Friedrich CP14-18-24 CP14N10 item
- safety signs and mark certificates which confirm compatibility with appropriate standards
Why don't we read the manuals?
Usually it results from the lack of time and certainty about functionalities of purchased items. Unfortunately, networking and start-up of Friedrich CP14-18-24 CP14N10 alone are not enough. An instruction contains a number of clues concerning respective functionalities, safety rules, maintenance methods (what means should be used), eventual defects of Friedrich CP14-18-24 CP14N10, and methods of problem resolution. Eventually, when one still can't find the answer to his problems, he will be directed to the Friedrich service. Lately animated manuals and instructional videos are quite popular among customers. These kinds of user manuals are effective; they assure that a customer will familiarize himself with the whole material, and won't skip complicated, technical information of Friedrich CP14-18-24 CP14N10.
Why one should read the manuals?
It is mostly in the manuals where we will find the details concerning construction and possibility of the Friedrich CP14-18-24 CP14N10 item, and its use of respective accessory, as well as information concerning all the functions and facilities.
After a successful purchase of an item one should find a moment and get to know with every part of an instruction. Currently the manuals are carefully prearranged and translated, so they could be fully understood by its users. The manuals will serve as an informational aid.
Table of contents for the manual
Ser vi ce & P ar ts Manu al 200 7 Compact Programmable Models CP14N10 CP18N30 CP24N30 CP-14-18-2[...]
2 T ab le o f Co n t en ts Per formanc e Data .....................................................[...]
3 Model CP14N10 CP18N30 CP24N30 Function COOLING COOLING COOLING Rated V oltage 1 15V ~ 230/2[...]
4 Out er Compo ne nt Ide n ti ﬁ ca ti on Models : CP1 4N 1 0 , CP 1 8N3 0, CP2 4N30 Cabinet Air [...]
5 Installat ion D imensions Models : CP1 4N 1 0 , CP 1 8N30, CP24 N30 (Top View) Fence / obstruction[...]
6 CP24N30 CP18N30 / CP14N10 Wirin g Dia gram s[...]
7 F unct ional C omponent De ﬁ niti ons MEC HANIC AL C OMPONEN TS Ve nt d o o r A l l o w s i[...]
8 In the c ase of the c apillar y tube thi s is acc omplished (by design ) throug h size ( and len[...]
9 EQUIP MENT RE QUIRED 1. Vo l t m e t e r 2. Ammeter 3. Ohmmeter 4. E.P . A . A pproved [...]
10 NOTE : I n o r d e r t o a c c e s s t h e s e a l e d sy s t e m i t w i l l b e n e [...]
11 A n u n d e r c h a r g e d s y s t e m w i l l r e s u l t i n p o o r p e r f o r m a n [...]
12 RESTRICTED REFRIGERANT SYSTEM A quick c he c k for either c ondit ion begins at t he evaporator [...]
13 Problem Possible Cause Action Compressor does not run Low voltage Check voltage at compressor[...]
14 Problem Possible Cause Action Unit does not run Fuse blown or circuit tripped Replace fuse, re[...]
15 Problem Possible Cause Action Compressor runs for short periods only . Cycles on overload Ov[...]
16 Problem Possible Cause Action W ater "spitting" into room Sublimation: [...]
17 Problem Possible Cause Action Room temperature uneven (Heating cycle) Heat anticipator (resis[...]
18 Problem Possible Cause Action Unit cools when heat is called for Incorrect wiring Refer to ap[...]
19 Com pon en ts Model CP 1 4N 1 0[...]
20 No Description Qty Friedrich Part# Code 1 Supporter Assy 1 67700200 2 Screw ST4.2X13 7 [...]
21 No Description Qty Friedrich Part# Code 37 Clapboard of Snail Shell 1 67700108 38 Base Pl[...]
22 No Description Qty Friedrich Part# Code 1 Supporter Assy 1 67700132 2 Self-threading Scre[...]
23 No Description Qty Friedrich Part# Code 36 Blower Wheel 1 677001 16 37 Front Clapboard of[...]
24 Com pon en ts Model CP2 4N30[...]
25 No Description Qty Friedrich Part# Code 1 Supporter Assy 1 67700200 2 Screw ST4.2X13 7 [...]
26 No Description Qty Friedrich Part# Code 38 Base Plate of Air Flue 1 67700106 39 Evaporat[...]
Friedrich Air Conditioning Company P.O. Box 1540 San Antonio, TX 78295 210.357.4400 www.friedrich[...]
CP-14-18-24-Svc-Prts-07 (3-07) F r iedrich Air Condition ing Co. Post Of f ice Box 15 4 0 • San An[...]