Bosch 14/19CBI manual
- Read online or download the manual
- 44 pages
- 0.82 mb
Go to page of
A good user manual
The rules should oblige the seller to give the purchaser an operating instrucion of Bosch 14/19CBI, along with an item. The lack of an instruction or false information given to customer shall constitute grounds to apply for a complaint because of nonconformity of goods with the contract. In accordance with the law, a customer can receive an instruction in non-paper form; lately graphic and electronic forms of the manuals, as well as instructional videos have been majorly used. A necessary precondition for this is the unmistakable, legible character of an instruction.
What is an instruction?
The term originates from the Latin word „instructio”, which means organizing. Therefore, in an instruction of Bosch 14/19CBI one could find a process description. An instruction's purpose is to teach, to ease the start-up and an item's use or performance of certain activities. An instruction is a compilation of information about an item/a service, it is a clue.
Unfortunately, only a few customers devote their time to read an instruction of Bosch 14/19CBI. A good user manual introduces us to a number of additional functionalities of the purchased item, and also helps us to avoid the formation of most of the defects.
What should a perfect user manual contain?
First and foremost, an user manual of Bosch 14/19CBI should contain:
- informations concerning technical data of Bosch 14/19CBI
- name of the manufacturer and a year of construction of the Bosch 14/19CBI item
- rules of operation, control and maintenance of the Bosch 14/19CBI item
- safety signs and mark certificates which confirm compatibility with appropriate standards
Why don't we read the manuals?
Usually it results from the lack of time and certainty about functionalities of purchased items. Unfortunately, networking and start-up of Bosch 14/19CBI alone are not enough. An instruction contains a number of clues concerning respective functionalities, safety rules, maintenance methods (what means should be used), eventual defects of Bosch 14/19CBI, and methods of problem resolution. Eventually, when one still can't find the answer to his problems, he will be directed to the Bosch service. Lately animated manuals and instructional videos are quite popular among customers. These kinds of user manuals are effective; they assure that a customer will familiarize himself with the whole material, and won't skip complicated, technical information of Bosch 14/19CBI.
Why one should read the manuals?
It is mostly in the manuals where we will find the details concerning construction and possibility of the Bosch 14/19CBI item, and its use of respective accessory, as well as information concerning all the functions and facilities.
After a successful purchase of an item one should find a moment and get to know with every part of an instruction. Currently the manuals are carefully prearranged and translated, so they could be fully understood by its users. The manuals will serve as an informational aid.
Table of contents for the manual
9 / 14CBi, 14 / 19CBi, 19 / 24CBi W ALL M OUNTED BOILERS FOR CENTRAL HEA TING AND INDIRECT SUPPL Y O[...]
1.1 Gas Safety (Installation & Use) R egulations 1998. It is the law that all gas appliances ar [...]
working at a gauge pr essure of at least 0.35bar abov e the relief valv e setting if on a sealed sys[...]
The data plate is fixed t o the inner casing cover . 4 3. T echnical Da ta HYDRA ULIC RESIST ANCE BO[...]
5 GAS SUPPL Y SYSTEM - BASED ON NG (G20) T OT AL LENGTH OF GAS SUPPL Y PIPE (COPPER) metres 3 6 9 12[...]
The appliance may be inst alled in any room subject t o the requir ements of the current IEE regulat[...]
The flue system must be inst alled following the requir ements of BS5440:1. The standar d flue kit l[...]
The system must comply with r equirements of BS6798 and BS5449. General: The appliance is only suita[...]
Heating return Non return valve Non return valve Hose union T est cock T emporary hose Stop cock Aut[...]
The gas supplier must be contacted t o check the suitability of the appliance for the local gas supp[...]
11 Fig.10. Boiler wiring diagram Flame Sense Electrode Spark Electrode Gas V alv e Air pressur e swi[...]
12 Fig.11 . Sy stem wiring diagram Control Boar d X1 Pump L Pump N P ermanent N P ermanent L Switche[...]
13 Fig. 12a. Boiler Assembly 9/14CBi Shown set for R ear Only flue kit 1. Inner case 2. J bolts and [...]
14 1. Inner case 2. J bolts and wing nuts (2) 3. Combustion chamber cov er 4. Burner 5. Burner fixin[...]
NO TE: READ THIS SECTION FULL Y BEFORE COMMENCING THE INST ALLA TION T o install a boiler with a rea[...]
16 11.1.5 Boiler Prepar ation (i) R emove the appliance casing b y releasing the scr ew at the centr[...]
17 1 1. Flue hood 2. Fan 3. Sensing connection ( + ) 4. Sensing connection (—) 5. T op outlet seal[...]
11.1.8 Completion of the Installation Check that all the gas and water connections ha ve been tighte[...]
11.2.5 Flue Prepar ation (i) Drill the hole for the flue at Ø1 1 0mm unless the optional internal f[...]
11.2.6 T elescopic Horizontal Flue Kit up to 750mm in Length (i) The standar d flue can be telescopi[...]
11.2.9 V ertical A daptor for Horizont al Flues An adapter is av ailable for an initial short sectio[...]
11.2.12 Installation of Flue ont o Boiler (i ) Fit the clamping ring around the flue spigot but leav[...]
Cleansing and Inhibiting a Central Heating Installation in compliance with Benchmark It is accepted [...]
12.8 Central Heating Check that the external controls ar e calling for heat to the heating cir cuit.[...]
F a n - Horizontal Flue. R emov e the combustion chamber cov er . Carefully pull off the electrical [...]
Important: T urn off the gas and electricity supplies and drain, where necessary , before r eplacing[...]
27 Fig. 34 . Inner Casing - Gas and Electric Controls. 9/14CBi shown. 2 3 1 1. Inner casing 2. J bol[...]
15.4.1 Gas V alve NO TE: If the left hand clearance is >50mm then the gas valv e can be replaced [...]
15.4.5 Control Boar d L ower the base plate/control assembly and car efully disconnect the plug-in c[...]
15.4.7 Air Flow Sensor R emove the f an as described in 14.3. Unscrew and withdr aw , through the f [...]
15.4.11 Combustion Chamber Insulation The insulation pads are manuf actured from a material in accor[...]
These instructions should only be read if conv erting appliance from Natur al Gas to LPG or vice ver[...]
1 E60-473 Burner Assembly NG 9/14CBi 1 8 7 1 6 12 1 773 0 Burner Assembly LPG 9/14CBi 1 8 7 1 6 1 0 [...]
34 18. Opera tional Flow Diagr am Mains 230V supply BOILER HEA T DEMAND Pump continues for 4 minutes[...]
35 19. F ault Finding NO TE : This fault finding information is f or guidance only . W or cester , B[...]
36 R emov e connector X5 and test resist ance between the red and violet cables. Is the resist ance [...]
F AIL POINT C Is the boiler in a very cold environment i.e is the primary water temperatur e below 5[...]
F AIL POINT E 'BURNER LOCK OUT' Is the gas supply connected and at the correct pr essure? [...]
39 F AIL POINT F Deliver ed primary water temperatur e alwa ys t oo hot. (Over 85°C) Deliver ed pri[...]
CONTROLS T o comply with the Building Regulations, each section must have a tick in one or other of [...]
SERVICE INTERVAL RECORD It is recommended that your heating system is serviced regularly and that yo[...]
This booklet is accurate at the date of printing but will be super seded and should be disregar ded [...]